Payment & Shipping Terms:
|Air Inlet:||Turbo Intercooled||Bore/Trip:||105/130|
|Name:||Diesel Generator 1500 Rpm||Place Of Origin:||Shandong China|
diesel engine generator set,
genset diesel generator set
|1. Specification of genset|
|Dimensions(mm) (L×W×H)||1850X720X1250mm||Open type|
|2. Specification of diesel engine|
|Number of Cylinders||6|
|Cylinder arrangement||Vertical in-line|
|Aspiration||Turbo INtercooled, Air/Water cooling|
|Cooling System||Forced Water Cooling Cycle|
|3. Specification of alternator|
|Number of Phase||3|
|Connecting Type||3 Phase and 4 Wires|
|Number of Bearing||1|
|Exciter Type||Brushless ,Self-exciting, AVR automatic voltage regulating,
100% Copper winding wire (Brush is also available)
|Telephone Influence Factor (TIF)||≤50|
|Voltage Regulation, Steady State||≤±1%|
|Transient State Voltage||≤-15%~+20%|
Installation requirements in machine room. Keep the machine room clean.A dry,Inlet and outlet air is clear.The unit must exhaust the air duct hood to prevent hot air from returning to the machine room;Muffler shallMust be properly hoisted,To avoid crushing the supercharger.When used in high dust environment,Not only in the machine room to install filters and dustproofNets keep out excess dust(unit water tank,Premature blockage of air filtration,Measures should also be taken to prevent the dust from entering the exhaust pipe.In the exhaust duct.
1. Select the oil that meets the requirements of the generator. Before starting the engine, check whether the oil level and cooling level are normalLocation, continuous boot operation4Check the oil level around the hour.
2. Choose the antifreeze or antirust solution approved by the manufacturer according to the ambient temperature.Add after adjusting to proportion;Don'tUse clean water only (rusting of engine channel, cavitation erosion, rust of thermostat, etc.).Add cooling fluid to generate electricityThe machine body exhausts air to prevent damage to the cylinder in the channel
3. The unit is forbidden to work under overload.The unit is strictly forbidden to be hit by large load.
4. Before the unit is shut down, load is discharged and no load is operated3 ~ 5Stop after a minute.The unit is not allowed to operate for a long time under low load or idle state.The spare unit should be operated without load at least once a month.Empty vessels carryingTurn time10to15Minutes;And the annual load (80%At least operation2to4Hours.
5. The power supply of the reserve unit should be charged regularly, and the electrolytic level of the battery should be checked at the same time. If not enough, it should be added in time (it can be steamedBoiling water).Check whether the connection of the battery line is firm. Do not connect the wrong way.
6. Operating personnel carefully complete the unit's operation, maintenance records.
Pakcing and delivery:
Weifang Best Power Equipment Co., Ltd.Is A Professional Manufacturer Who Specialized In Manufacturing, Researching And Development Of Diesel Generator Set Offering Efficient, Safe, Stable And Diesel Generator Set Solutions.For More Than A Decade, Bst Has Been Focusing On Products. From A Single Product Manufacturer, Now We Are Already Growing Up To A Company With Advanced Hardware Like Generator Engineering Technology Research And Development Center, Also A Number Of Experts Standby. We Are Also A State-Level High-Tech Enterprises With Rich Experience Of Product Customization. Bst Sincerely Welcomes All Customers To Come To Us
Contact Person: jacky