Payment & Shipping Terms:
|Air Inlet:||Turbo Intercooled||Bore/Trip:||105/130|
120KW / 150KVA 6 Cylinder Water Cool Small Diesel Generator Set Genset Low Noise
Weifang Best Power Equipment Co.,ltd founded in Apri-24th 2014 . The company is a production , sale , import and export trade in an integrated enterprise, with independent legal person qualification. Main business: 10KW--2000KW diesel engine which used for generator, drainage and irrigation equipment, fire unit,and the ship . We started as a diesel engine factory with 7000sets production yearly ,now have become one of the leading suppliers in the diesel / gas generator and diesel pump field in China.
|1. Specification of genset|
|Dimensions(mm) (L×W×H)||1850X720X1250mm||Open type|
|2. Specification of diesel engine|
|Number of Cylinders||6|
|Cylinder arrangement||Vertical in-line|
|Aspiration||Turbo INtercooled, Air/Water cooling|
|Cooling System||Forced Water Cooling Cycle|
|3. Specification of alternator|
|Number of Phase||3|
|Connecting Type||3 Phase and 4 Wires|
|Number of Bearing||1|
|Exciter Type||Brushless ,Self-exciting, AVR automatic voltage regulating,
100% Copper winding wire (Brush is also available)
|Telephone Influence Factor (TIF)||≤50|
|Voltage Regulation, Steady State||≤±1%|
|Transient State Voltage||≤-15%~+20%|
Diesel generator use method and matters needing attention
1.Installation requirements in machine roo. Keep the machine room clean.A dry,Inlet and outlet air is clear.The unit must exhaust the air duct hood to prevent hot air from returning to the machine room;Muffler shallMust be properly hoisted,To avoid crushing the supercharger.When used in high dust environment,Not only in the machine room to install filters and dustproofNets keep out excess dust(unit water tank,Premature blockage of air filtration,Measures should also be taken to prevent the dust from entering the exhaust pipe.In the exhaust duct.
2.1Select the oil that meets the requirements of the generator. Before starting the engine, check whether the oil level and cooling level are normalLocation, continuous boot operation4Check the oil level around the hour.
2.2Choose the antifreeze or antirust solution approved by the manufacturer according to the ambient temperature.Add after adjusting to proportion;Don'tUse clean water only (rusting of engine channel, cavitation erosion, rust of thermostat, etc.).Add cooling fluid to generate electricityThe machine body exhausts air to prevent damage to the cylinder in the channel
2.3The unit is forbidden to work under overload.The unit is strictly forbidden to be hit by large load.
2.4Before the unit is shut down, load is discharged and no load is operated3 ~ 5Stop after a minute.The unit is not allowed to operate for a long time under low load or idle state.The spare unit should be operated without load at least once a month.Empty vessels carryingTurn time10to15Minutes;And the annual load (80%At least operation2to4Hours.
2.5The power supply of the reserve unit should be charged regularly, and the electrolytic level of the battery should be checked at the same time. If not enough, it should be added in time (it can be steamedBoiling water).Check whether the connection of the battery line is firm. Do not connect the wrong way.
2.6Operating personnel carefully complete the unit's operation, maintenance records.
3.1Unit operation200to300Oil must be changed every hour or every year. Oil must be removed at the same timeDevice (including bypass).Oil should be used for the first time or under harsh conditions100Change within hours.
3.2The engine's air filter is available500Change in an hour or two;More dust and other harsh environmental conditions will be greatly reducedThe cycle of empty filter, observe the position indicated by the empty filter blocker, indicate that it must be replaced when entering the red area.
3.3The coolant is replaced every two years, and the coolant filter should be replaced annually.
3.4The quality diesel must be chosen in line with national standards.The first care should be cleaned regularly, with fine aluminum for each use500Hours should be replaced.With oilWater separator unit each use50Drain or replace the filter element regularly around the hour.
3.5Never reuse the engine after cleaning.Select pure engine filters and components.
Why choose us?
1. Original Factory We Are . we have a large stock and Spare Part Warehouse .
2. 2KW--2000KW diesel engine which used for generator, drainage and irrigation equipment, fire unit,
and the ship.the voltage is 220/380V,230/400V,240/415V or as your request.
3.Top Quality Engine with Famous Brand Alternator(Stanford,Marathon,well-know brands at home and abroad.)
4. With competitive price. More order, more discounts will get !
5. Best after-sales services : whole life technical support and one year warranty time.
6. Fast delivery time : in 10 days after get the deposit.
Our service :
1. Help Customers find out the suitable power of the diesel generator.
2. Show the detail specifications to customers to choosen.
3. Help customers figure out the freight and arrange it.
Diesel generator can be used in many different situations. It can meet different requirements.
1. What's the power range of diesel generator?
Answer: Power range from 18-2000kw,23-2500kva.
2. What's the delivery time?
Answer: in 10 days after get the deposit.
3. What's the payment term?
Answer: we accept T/T,and 30% T/T as the deposit,the balance should be paid before delivery.
irrevocable L/C at sight.
4. What's your warranty?
Answer: 1000 working hours or 1 year whichever comes first.
5. What's your MOQ?
Answer: 1 set
6. What's the frequency of diesel generator set?
7. What's the voltage of your diesel generator set?
Answer: the voltage is 220/380V,230/400V,240/415V or as your request.
Contact Person: jacky