Payment & Shipping Terms:
|Modle Number:||K4100D||Speed Way:||Mechanics|
|Number Of Bearing:||Single||The Rated Power:||30kw|
|Name:||Industrial Diesel Generator||Origin:||Weifang Shandong|
30kw 37.5kva Small Power 1500 Rpm Diesel Generator Three Phase Generator
|1. Specification of genset|
|Dimensions(mm) (L×W×H)||1700x800x1150mm||Open type|
|2. Specification of diesel engine|
|Number of Cylinders||4|
|Cylinder arrangement||Vertical in-line|
|Aspiration||Natural aspiration, Air/Water cooling|
|Cooling System||Forced Water Cooling Cycle|
|3. Specification of alternator|
|Number of Phase||3|
|Connecting Type||3 Phase and 4 Wires|
|Number of Bearing||1|
|Exciter Type||Brushless ,Self-exciting, AVR automatic voltage regulating,100% Copper winding wire (Brush is also available)|
|Telephone Influence Factor (TIF)||≤50|
|Voltage Regulation, Steady State||≤±1%|
|Transient State Voltage||≤-15%~+20%|
Diesel generator operation
1.Select the oil that meets the requirements of the generator. Before starting the engine, check whether the oil level and cooling level are normalLocation, continuous boot operation4Check the oil level around the hour.
2.Choose the antifreeze or antirust solution approved by the manufacturer according to the ambient temperature.Add after adjusting to proportion;Don'tUse clean water only (rusting of engine channel, cavitation erosion, rust of thermostat, etc.).Add cooling fluid to generate electricityThe machine body exhausts air to prevent damage to the cylinder in the channel
3.The unit is forbidden to work under overload.The unit is strictly forbidden to be hit by large load.
4.Before the unit is shut down, load is discharged and no load is operated3 ~ 5Stop after a minute.The unit is not allowed to operate for a long time under low load or idle state.The spare unit should be operated without load at least once a month.Empty vessels carryingTurn time10to15Minutes;And the annual load (80%At least operation2to4Hours.
5.The power supply of the reserve unit should be charged regularly, and the electrolytic level of the battery should be checked at the same time. If not enough, it should be added in time (it can be steamedBoiling water).Check whether the connection of the battery line is firm. Do not connect the wrong way.
6.Operating personnel carefully complete the unit's operation, maintenance records.
1.What's the power range of diesel generator?
Answer:Power range from 18-2000kw,23-2500kva.
2.What's the delivery time?
Answer:in 10 days after get the deposit.
3.What's the payment term?
Answer:1.we accept T/T,and 30% T/T as the deposit,the balance should be paid before delivery.
2.irrevocable L/C at sight.
4.What's your warranty?
Answer:1000 working hours or 1 year whichever comes first.
5.What's your MOQ?
6.What's the frequency of diesel generator set?
7.What's the voltage of your diesel generator set?
Answer:the voltage is 220/380V,230/400V,240/415V or as your request.
Contact Person: jacky