Payment & Shipping Terms:
|Air Inlet:||Turbo Intercooled||Bore/Trip:||105/130|
100KW / 125KVA Water Cooled Diesel Generator , 3 Phase Diesel Generator
1. If you are interested in our products we sincerely invite you to take a visit of our factory when you are in China. We can drive to pick you up and visit our factory.
2. Suggest the best choice or referential suggestion based on customers’ information. Answer all questions about the product from customer.We will supply the best plan for you according to your requirements.
3. Build customers’ profiles, follow-up service, make regular calls on customers,try our best to meet your demands.
4.24hours service on line,just the best service.
|1. Specification of genset|
|Dimensions(mm) (L×W×H)||1850X720X1250mm||Open type|
|2. Specification of diesel engine|
|Number of Cylinders||6|
|Cylinder arrangement||Vertical in-line|
|Aspiration||Turbo INtercooled, Air/Water cooling|
|Cooling System||Forced Water Cooling Cycle|
|3. Specification of alternator|
|Number of Phase||3|
|Connecting Type||3 Phase and 4 Wires|
|Number of Bearing||1|
|Exciter Type||Brushless ,Self-exciting, AVR automatic voltage regulating,
100% Copper winding wire (Brush is also available)
|Telephone Influence Factor (TIF)||≤50|
|Voltage Regulation, Steady State||≤±1%|
|Transient State Voltage||≤-15%~+20%|
Installation requirements in machine room. Keep the machine room clean.A dry,Inlet and outlet air is clear.The unit must exhaust the air duct hood to prevent hot air from returning to the machine room;Muffler shallMust be properly hoisted,To avoid crushing the supercharger.When used in high dust environment,Not only in the machine room to install filters and dustproofNets keep out excess dust(unit water tank,Premature blockage of air filtration,Measures should also be taken to prevent the dust from entering the exhaust pipe.In the exhaust duct.
1.Select the oil that meets the requirements of the generator. Before starting the engine, check whether the oil level and cooling level are normalLocation, continuous boot operation4Check the oil level around the hour.
2.Choose the antifreeze or antirust solution approved by the manufacturer according to the ambient temperature.Add after adjusting to proportion;Don'tUse clean water only (rusting of engine channel, cavitation erosion, rust of thermostat, etc.).Add cooling fluid to generate electricityThe machine body exhausts air to prevent damage to the cylinder in the channel
3.The unit is forbidden to work under overload.The unit is strictly forbidden to be hit by large load.
4.Before the unit is shut down, load is discharged and no load is operated3 ~ 5Stop after a minute.The unit is not allowed to operate for a long time under low load or idle state.The spare unit should be operated without load at least once a month.Empty vessels carryingTurn time10to15Minutes;And the annual load (80%At least operation2to4Hours.
5.The power supply of the reserve unit should be charged regularly, and the electrolytic level of the battery should be checked at the same time. If not enough, it should be added in time (it can be steamedBoiling water).Check whether the connection of the battery line is firm. Do not connect the wrong way.
6.Operating personnel carefully complete the unit's operation, maintenance records.
1.Unit operation200to300Oil must be changed every hour or every year. Oil must be removed at the same timeDevice (including bypass).Oil should be used for the first time or under harsh conditions100Change within hours.
2.The engine's air filter is available500Change in an hour or two;More dust and other harsh environmental conditions will be greatly reducedThe cycle of empty filter, observe the position indicated by the empty filter blocker, indicate that it must be replaced when entering the red area.
3.The coolant is replaced every two years, and the coolant filter should be replaced annually.
4.The quality diesel must be chosen in line with national standards.The first care should be cleaned regularly, with fine aluminum for each use500Hours should be replaced.With oilWater separator unit each use50Drain or replace the filter element regularly around the hour.
5.Never reuse the engine after cleaning.Select pure engine filters and components.
Pakcing and delivery:
1. What's the power range of diesel generator?
Answer: Power range from 18-2000kw,23-2500kva.
2. What's the delivery time?
Answer: in 10 days after get the deposit.
3. What's the payment term?
Answer: we accept T/T,and 30% T/T as the deposit,the balance should be paid before delivery.
irrevocable L/C at sight.
4. What's your warranty?
Answer: 1000 working hours or 1 year whichever comes first.
5. What's your MOQ?
Answer: 1 set
6. What's the frequency of diesel generator set?
7. What's the voltage of your diesel generator set?
Answer: the voltage is 220/380V,230/400V,240/415V or as your request.
Contact Person: jacky